Place of Origin : China
Brand Name : BaoShiDa
Model Number : FL001
Certification : CCC,ISO
Price : $1/m
Packaging Details : according to customer request
Delivery Time : 15 days after payment
Payment Terms : T/T 30% in advance, 70% before shipment
Supply Ability : 1000000/
MOQ : 500m
H07R-F wind power oil resistant ground protection cable is applicable for free hanging or fixed installation in fin cabin.
Type and Name
Wind Power oil resistant Ground Protection Cable
Ambient air temperature: Perennial mean temperature: 10℃
Extreme high temperature: 50℃
Extreme low temperature: -42℃
Average relative humidity: normal value for accumulated year: 80%
Earthquake Proof: Horizontal acceleration: 0.2g
Normal acceleration: 0.1g
Safety factor: 1.67
Note: g is acceleration of gravity. g=9.8m/s²
Extreme wind speed:30.0m/s
Range of Laying
Cables mainly lay in the cabin of fan, where machinery oil may leak or overflow.
Rated Voltage U0/U: 450/750V
Continues operating temperature:
Min. ambient temperature when laying: -5℃
Min. bending radius :
d: outer diameter
Conductor should comply with the requirements for Class 5 specified in IEC60228.
The surface of conductor should be bright and clean no grease, no burr or bulge or faulted wire to damage the insulation.
Every conductor coat with an isolated layer made from appropriated material.
The nominal value for thickness of sheath should comply with DIN VDE 0282-4. Meanwhile, the average value of should be no less than nominal value while the thinnest part should be no less than 85%-0.1mm of the nominal value.
Sheath is made from oil-resist insulated PVC, whose properties should comply with requirements for 3GI3 specified in DIN VDE 0207 T20. The sheath should tightly rapped on stranded insulated core or coating. Meanwhile, the outer sheath should be clean and color evenly.
Insulated conductors are separated by color yellow and green, and in accordance with requirements of DIN VDE 0293.
The ohmic value of conductor should be no more than specifications in IEC60228 at 20℃.
Finished cables and insulated cores should withstand the rated AC voltage test of 2500V, and no breakdown in five minutes.
The resistance of insulated conductor should be no more than 20MΩ•km.
Mechanical and physical properties for finished cable sheath should comply with requirements in DIN VDE 0282-4.
Finished cables should withstand the burning test specified in EN50265-2-1 or IEC60332-1.
Finished cables should withstand the oil-resist test specified in DIN VDE 0473 6081-2-1.
Products can leave factory only after passing examination of technology department. Each package should be shipped with the product quality inspection certificate.
Products should inspect according to DIN VDE 0282-4. If it fails for the first time in sample inspection, then take another two samples to examine the failed project. If the two samples are acceptable, then the products are acceptable, false otherwise. The number of samples is accepted by both sides, or decided by manufacture at the time of no requirements from the buyer.
Mark、Packing、Transport and Storage
There should be marks of maker, type, nominal cross-section area, voltage on the cable. The marks should comply with the requirements for conductor and color specified in DIN VDE 0293-308.
Marks shall be legible, not easy to erase. The writing should be clearly visible after 10 times graze in absorbent cotton cloth.
Cables can be packed both in coils and in circles. Cables in circle should be packed on cable specified in JB/T8137. Cables should be positive sealing, for those outside the circle, protective cover should be made. And the length of outside should be no more than 300mm.
Tags should identify:
① Maker or trade-mark
② Type and specifications mm²,V
③ Lengths m
④ Manufacturing Date: Year Month
⑤ Product Standard Code
⑥ Correct direction for circles
Transport and Storage
The cables should avoid high temperature and cable circle does not allow flat.
Forbid throwing circles with cable from high attitude and mechanical damage.
Forbid lifting several circles at the same time. Circles should be put firm with appropriate methods to avoid tip over.
H07R-F Wind Power oil resistant Ground Protection Cable Images